Good article, but it fails to point out that leaky return-side ducts could be drawing dust and allergens into the duct system from the enclosed spaces in which they run, e.g. between walls, below floors, attic. So duct cleaning may only be a temporary solution. The homeowner can get a home energy audit -- free in many states -- to determine if they have significant duct leakage. An Aeroseal dealer may be able to effectively seal up the duct system without needing to tear into walls etc to get to the ducts.
Greetings from Mama Duck from Ductz of Greater Atlanta. These are some awesome comments and a few are from high quality duct cleaners that I personally know. After 19 years in this industry I agree that a government agency is not always up to date with their knowledge but won't admit it. If they were out in the field with our technicians every day they would upgrade their info. I get calls all the time where customers have been taken advantage of by "go and blow" companies. The customers don't know what they don't know but many are too lazy to do the research and are just looking for cheap. The industry has gotten a bad rap due to these con artists but the customer has to take some responsibility. I ask them why they would want to do business with a company who lies to them in print? Are they stupid or just cheap? Thankfully there are those of us in the industry who are working diligently to raise the bar on quality, protect the consumer and perform high quality work. At Ductz all our technicians are NADCA certified, trained by the best in the industry and know how to clean the entire system.
An air conditioning system's SEER is especially important if you live in a climate that changes temperature dramatically. The SEER is determined by the cooling output during the winter divided by its electric input during the winter. The higher the rating, the more efficient it will be. In January of 2006, the U.S. put standards in place for cooling units which are still in effect today. They must have a minimum SEER of 13. So, if you live in a home with a system installed before the new standards went into effect, consider having it replaced. SEER 13 units increase home efficiency by 30 percent.
Ok what you said is true but in most cases ducts are in a duct flex format, and knowing that the dust in people's flex duct is just surface dust, any real debris that are in the duct itself will result in very little to no air flow which will keep your unit from performing properly, but if it is true allergy reasons then replacing your duct system is better for overall better air quality, plus if you do pay attention to the warranty on flexible duct is that it only has a 10 year warranty and typically only lasts for 20 years so do your research before having a duct cleaning, and to add one more thing if your duct work is completely metal and you can't see visible insulation then your duct on the inside has insulation inside of it, if you replace that with duct work that is clean metal on the inside and wrapped with insulation on the outside then it will further reduce the air bourne fiberglass and dust.
A year and a half ago (fall of 2015) we replaced the furnace and air conditioner. From what we could determine this was the third forced air furnace and second air conditioner unit for the house. As part of the installation, we changed out the two 6″ ducts feeding the second floor with 8″ ducts. The idea was to get more cold air to the second floor in the summer. It worked and for the first time the second floor and first floor temperatures were the same when the air conditioner was running. Of course, to make the system work I close down upstairs duct damper doors in the winter and open them up in the summer.
CIBSE publishes several guides to HVAC design relevant to the UK market, and also the Republic of Ireland, Australia, New Zealand and Hong Kong. These guides include various recommended design criteria and standards, some of which are cited within the UK building regulations, and therefore form a legislative requirement for major building services works. The main guides are:
Some systems include an "economizer mode", which is sometimes called a "free-cooling mode". When economizing, the control system will open (fully or partially) the outside air damper and close (fully or partially) the return air damper. This will cause fresh, outside air to be supplied to the system. When the outside air is cooler than the demanded cool air, this will allow the demand to be met without using the mechanical supply of cooling (typically chilled water or a direct expansion "DX" unit), thus saving energy. The control system can compare the temperature of the outside air vs. return air, or it can compare the enthalpy of the air, as is frequently done in climates where humidity is more of an issue. In both cases, the outside air must be less energetic than the return air for the system to enter the economizer mode.
I am NADCA Certified Air Systems Cleaning Specialist. Over the year I have learned on simple answer to this questions: there air duct cleaners and there are pretenders. There will be no benefit at all if you use on the very cheap pretender because they will not really clean anything. On the other hand if you call a qualified air duct cleaner with a NADCA Certification you will, like 99% of my customers, report improvement with your respiratory problems, you will see less dust and the job will pay for itself with energy savings and repair prevention.
Two weeks go by and no phone call from HVAC Service regarding install date, or any update at all. I call them to check in to see if they have put me on the schedule and when I can expect to have the AC installed. You can tell by the discussion I had with the lady on the phone that they completely forgot about me and have not scheduled anything. She says she needs to get in contact with the owner because she has no idea on the availability of the crane. I was told that she would call me back by the end of the day with an update. Surprise, surprise, no phone call.
DIY: Most DIY installations go smoothly. The major brands have compatibility checkers to see which of their models will work with the wiring your old thermostat is using. Potential problems involve the need for a C-wire, or common wire, when the existing bundle doesn’t include one. There are solutions discussed in our Thermostat Buying Guide, linked to below.
This is where i found where the major problem was for the dust problem in my home. I took down the sheet metal that was 16" wide down by taking the screws out that keep it attached and when i took it down i, could not beleive the amountbof dust that was up there, inhad to put on breathing nasks to actually scoop out all the cust with my hads and then i used my shop vac then bleached everything, i would say that i filled up a 5 gallon maybe more not counting all the dust that was attached to the side of the beams that was all wood , because the contractor did not actually build a 16" wide return all out of metal , butvinstead used the sheet metal plate as a short cut to make a suare box using my beams in my basement to make a suare box. I was told contractors do that often and i feel that should be outlawed because it caused my sinus and allery problems,nwhich almost caused me to die. so everyone should make sure their ductwork was made properly. Yes seal it . Cover all openings. So it was not the contractors fault that my vents still had dust, in them, he was afraid tomgetvon top of my pool table to try to get iside the short cut ductwork with the 16" wide sheet metal. To everyone, make sure you clean your vent system. And make sure you could see it visually like i did , neither i or the contractor had no clue the problem was right above my pool table because of the make shift ductwork. The contactor shoul have made a squrae duct like the rest instead of using my beams as a short cut. That could be whyba lot of people start to have major allergy problems and maybe even ashma.so coverall holes to prevent dust to be taken in and all bugs etc. then make sure you clean your ductwork as you see reasonable, they say every 5 years , but i say evry 2 to 3 years, but you can do it yoursely.. You need a good air hose and suction vacum like a shop vac, do a little research. I invented something a while back like 18 to 20 years ago , and now it is on the market to help homeowners such as ourselves with this dust problem. I cannont say anymore because i have to make sure that it was not my research and idea that solved my problem and for all the others that are using what i invented ..there was nothing on the patent search that i hired an invention company to do, back then. Once yor vents are cleaned properly younwill be very happybif you are an allery sufferer. Stop the children for throwing things into the ductwork and sweeping things into the ductwork, keeping your vent system is clean once youbclean it right the first time, just maintain it , you dhould keepmthe hvac system clean such as coils etc it truly helps,people vome into my condo and they cannont beleive how cold it igets and how my system works so well. it is because i have my whole duct system sealed outsid with the duct sealant and my coils i vleaned my self and take the time that the furnase fan is cleaned because that could have a lot of major dust attached to it, mine had a lot of caked on dust it was like hard dirt. Yxounwill save on allergy bills nasal sprays, i wish I could say more because incould say something to really keep your whole duct system clean for years once you do a first good cleaning of intake and return vents. until i email one of the major companies to see where they got my idea from. Intrulybhope it was not from the invention company i hired years ago who did the patent search for my idea. I becam
Replacing a capacitor is easy. Just take a photo of the wires before disconnecting anything (you may need a reference later on). Then discharge the stored energy in the old capacitor (Photo 4). Use needle-nose pliers to pluck one wire at a time from the old capacitor and snap it onto the corresponding tab of the new capacitor. The female crimp connectors should snap tightly onto the capacitor tabs. Wiggle each connector to see if it's tight. If it's not, remove the connector and bend the rounded edges of it so it makes a tighter fit on the tab. When you've swapped all the wires, secure the new capacitor (Photo 5).