I to had an odd layer of white'ish dust building up especially during seasonal periods when the HVAC ran a a lot. I carefully swept up the fine dust into a small pile and had it analyzed. Turns out it was very fine fiberglass powder dust. It turns out it is the insulation form the attic! (My attic has blown in insulation). Turns out if you (I) had small gaps around my HVAC registers in the ceiling whee the airs blows into the room. What occurred in my case was that the exiting air at that seam creates a vacuum effect at the grate vent cover and draws and then blows fine insulation dust from the attic into the house. Removing each register grate and sealing each tin outlet gap with calking between the dry wall ceiling and tin fixed the issue. A couple were so bad with bowed gaps I had to screw down the bowed tin to the attaching stud better. Checking the very same glass top desk that catches and shows any dust accumulation now shows only very small amounts of normal house dust build up over several weeks. A big, big improvement. You might have a look by simply removing a couple vent covers yourself.
We installed a TRANE XL18 HVAC with a TRANE HV80 furnace 16 years ago and it still works great in Tucson, AZ. We inquired into a replacement for the future since the R-22 refrigerant will be off market at the end of this year. Our maintenance folks want to sell me a new system anyway (even though the TRANE works great). We are considering the BOSCH Inverter heat pump as a lower cost option down the road. Watch out for the tricky salesmen trying to sell beer at champagne prices though. Get estimates on whether you need to replace your current system and how much it could cost. And if they are factory certified.
The original furnace was a coal fired “octopus” design which had no blower to circulate the air but relied upon warm air rising to distribute the heat. That also means that the system breathed air in from the basement and most of this type did not have a cold air return system. At some point (probably in the 1940’s) the system was upgraded to a forced air gas furnace. The upgrade included replacing the 12″ diameter air ducts exposed in the basement with 6″ ducts and a cold air return system of ducts from the two (only two) air returns on the first floor.
This article was very good. It should be noted that the EPA building in Washington, DC, was cited years ago as one of the worst "sick building syndrome" buildings. Wish you had mentioned about having people's dryer vents cleaned since they can cause so many fires in homes. Most homeowners forget to check the air flow on the dryer vent. Our company, which cleans by NADCA standards, does both air ducts and dryer vents. Thanks again for keeping the public informed, especially regarding the cost of air duct cleaning...you get what you pay for...don't be fooled by the lowest cost out there. Frequently these are bait and switch companies or will keep adding on features they say a customer needs until the price is so high it's ridiculous.
Appliance Repair in Fayetteville Appliance Repair Santa Barbara Lansing, MI Appliance Repair Augusta, GA Appliance Repair Appliance Store Raleigh York Appliance Repair Appliance Repair Austin Appliance Repair Topeka Appliance Repair Louisville Appliance Repair Salem, NH Paducah, KY Appliance Repair Evansville Appliance Repair Toms River, NJ Appliance Repair Appliance Repair in Easton, PA