Preventing against air leakage is great, but the only way to keep dust and debris out of a duct system would be to completely seal off the return-air side of the system, which would render the system useless. Cold-air returns will always pull dust and other particles into the system. A high-MERV rated filter is definitely a good idea, but it does nothing to keep the return side of the system clean. Definitely agree though to use foil tape to seal seams, etc. Duct tape dries out over time and as it does can actually add more particles to the air.
Some systems include an "economizer mode", which is sometimes called a "free-cooling mode". When economizing, the control system will open (fully or partially) the outside air damper and close (fully or partially) the return air damper. This will cause fresh, outside air to be supplied to the system. When the outside air is cooler than the demanded cool air, this will allow the demand to be met without using the mechanical supply of cooling (typically chilled water or a direct expansion "DX" unit), thus saving energy. The control system can compare the temperature of the outside air vs. return air, or it can compare the enthalpy of the air, as is frequently done in climates where humidity is more of an issue. In both cases, the outside air must be less energetic than the return air for the system to enter the economizer mode.
"Customer service was great, and the price was in-line with other places, and fast service. We had a whole replacement of the outside and inside. I would have liked to see a better install for the furnace and new thermostat - the new thermostat should have gone where the old one was, and even tho the new furnace was a tight fit, they didn't offer to come back and repair the case molding, or give me a discount on the damage done, and I believe they should have put a disconnect box on the outside of the home, to make it easier for any future repairs needed. Other than that, am very happy with the cooling and heating!"