They were quick to come out and diagnose the problem with my furnace, but I thought the estimate of $549 a bit high to replace the circuit board. So called around and found Leo's Appliance in Concord that sells appliance parts and the circuit board was only $90.49 - that is the retail cost to me, so I imagine the wholesale cost is a lot less. So BEWARE of this company since they wanted $500!!! to replace the circuit board which is located right in the front of the furnace - extremely easy to access. I hate it that you cannot trust repair companies.
Hello, I read your comment and I know it was two years ago but I hope you see my message. I am trying to figure out what to do as I was told that there is some cat odor in the finished basement. I think with the air conditioning running that it may carry odor. The litter boxes are always kept clean. I wonder if odor can be trapped in the ducts, if Air Duct Cleaning could help, but it is quite expensive plus I'm concerned that it may not help. Please elaborate as to why you think it doesn't work that well. Do you have any other advise? Did you work in the field of Air Duct Cleaning? Thanks so much!
I paid $49 for a groupon. When the guy came today, he did an inspection first and said the ductwork first needed to be treated for mold; $348 for a spray that would last 8 months or $680 for an UV light purifier that would last 2 years. Also, the furnace needed to be cleaned for another $260. When I told him to just clean the ductwork, he said I would owe an additional $305 because the groupon was only good for 1 return and I had 2. I sent him packing with no services performed. Thankfully I am only out of $49! I will complain to groupon.
If the condenser coils are clogged, the compressor can overheat and shut down. You'll experience intermittent periods of minimal cooling, followed by no cooling. Even if you're “sure” the condenser coils are clean, clean them again. Turn off the power. Flip the air conditioning service and furnace circuit breakers in your main electrical panel to the “Off” position. Next, turn off the power switch right at the furnace or air handler. Then yank the disconnect block (Photo 1) and clean the condenser coils (Photo 2). If the air conditioning service still doesn't work properly after you've cleaned the condenser coils, installed a new filter and opened all the supply vents, proceed with the following repairs. Your AC won't work fully unless you do this.