Reinstall the access panel and disconnect block. Turn on the circuit breaker and furnace switch. Then set the thermostat to a lower temperature and wait for the AC to start (see “Be Patient at Startup,” below). The compressor should run and the condenser fan should spin. If the compressor starts but the fan doesn't, the fan motor is most likely shot. Shut off the power and remove the screws around the condenser cover. Lift the cover and remove the fan blade and motor (Photo 7). Reinstall the blade and secure the cover. Then repower the unit and see if the fan starts. If it doesn't, you've given it your best shot—it's time to call a pro.
"Customer service was great, and the price was in-line with other places, and fast service. We had a whole replacement of the outside and inside. I would have liked to see a better install for the furnace and new thermostat - the new thermostat should have gone where the old one was, and even tho the new furnace was a tight fit, they didn't offer to come back and repair the case molding, or give me a discount on the damage done, and I believe they should have put a disconnect box on the outside of the home, to make it easier for any future repairs needed. Other than that, am very happy with the cooling and heating!"