In addition, the black dust was found in most of the heat registers. He could rub it off on his fingers but did nothing but spray compressed air on it which didn’t make it disappear since it wasn’t loose. Also, in the register in the basement he described the black dust as being oily. The reality of that situation is that I had the AC on until the morning of the service and minutes after he snaked the hoses in my back door it started raining. The basement register had condensation from the humidity all over it. It was not oily but wet. He asked for an old towel and wiped it out. Never saw anything so black – because I never had to clean soot. That is what I have in my ducts. Soot from years of the old coal furnace.
In variable climates, the system may include a reversing valve that switches from heating in winter to cooling in summer. By reversing the flow of refrigerant, the heat pump refrigeration cycle is changed from cooling to heating or vice versa. This allows a facility to be heated and cooled by a single piece of equipment by the same means, and with the same hardware.
"OTHER THAN A SMALL SCHEDULING HICK-UP THEIR SERVICE WAS EXCELLENT. JOSH THE TECHNICIAN THAT PREFORMED THE DIAGNOSTICS AND REPAIR WAS EXTREMLEY PROFESIONAL AND FRIENDLY â ¦ HE WAS ABLE TO FIND THE PROBLEM WHICH WAS VERY DIFFICULT TO FIND AND FIX THE PROBLEM. I WISH THAT ALL HOME SERVICE PEOPLE WERE AS GOOD AS HE WAS. I WOULD HIRE AGAIN...JOB WELL DONE !!!"