Dehumidification (air drying) in an air conditioning system is provided by the evaporator. Since the evaporator operates at a temperature below the dew point, moisture in the air condenses on the evaporator coil tubes. This moisture is collected at the bottom of the evaporator in a pan and removed by piping to a central drain or onto the ground outside.
If you don't agree with duct cleaning, fine. If there are some things that HVAC people can do to make the system need cleaning less often fine, but to suggest that I need to GO TO JAIL????? If you need to knock others to make yourself look better....... If duct cleaning is such a scam, why are their governing bodies like NADCA (which I do NOT belong to),several manufacturers of equipment, and national restoration franchises (I'm not a franchise either) who provide this service? I guess the whole world is stupid and only HVAC people are smart. I suppose I am scamming them when I clean puff backs, water damage, fire damage, and clean their carpets too? Or did I wake up one morning and say "ya know, it is great to be a hard working, honest owner operator, but I would love to provide a service that unlike everything else I do is a con and rips off the 90% referral business I busted my butt to earn"
Did not realize cost had gone up so much for this service. Two years ago I had furnace and ducts cleaned at my old house and it was under $400. Now the cost is $700 for this house. I will keep looking for someone to offer a lower price, check them out, and have it done. Or will find the paperwork to see who did it before. I liked this article and did learn some things. Thanks.
Demand controlled kitchen ventilation (DCKV) is a building controls approach of controlling the volume of kitchen exhaust and supply air in response to the actual cooking loads in a commercial kitchen. Traditional commercial kitchen ventilation systems operate at 100% fan speed independent of the volume of cooking activity and DCKV technology changes that to provide significant fan energy and conditioned air savings. By deploying smart sensing technology, both the exhaust and supply fans can be controlled to capitalize on the affinity laws for motor energy savings, reduce makeup air heating and cooling energy, increasing safety and reducing ambient kitchen noise levels.
Replacing a capacitor is easy. Just take a photo of the wires before disconnecting anything (you may need a reference later on). Then discharge the stored energy in the old capacitor (Photo 4). Use needle-nose pliers to pluck one wire at a time from the old capacitor and snap it onto the corresponding tab of the new capacitor. The female crimp connectors should snap tightly onto the capacitor tabs. Wiggle each connector to see if it's tight. If it's not, remove the connector and bend the rounded edges of it so it makes a tighter fit on the tab. When you've swapped all the wires, secure the new capacitor (Photo 5).
The answer to your question is most likely "Yes," but not defiitely. It depends on where the dust is coming from. Now, if your house is more than say, 12 years old then you likely do have leaks in your ducts that can let in insulation particles and dust from your attic. If this is the case then cleaning of the ducts-PROPER CLEANING, which like the article sas doess include EVERYTHING that the conditioned air passes through, such as your indoor evaporator coil and blower housing assembly-is definitely a good first step to getting that dust under control! Of course I highly recommend that you also have your ducts SEALED as well, or else you will have to repeat the cleaning some time down the line. As a 3rd step, consider an electronic air filter. I always thought they were a scam, personally, so I never bothered selling them to my clients. Then one day my manager sent me to install one for a senior couple in a mobile home. The wife had bad allergies, and her eyes were constantly watering and puffy and red. Well, I did a quality check 60 days later and she could not stop praising that air filter! Keep in mind that in a mobile home, duct seals are not as complete as those in other homes due to access issues.
I recently replaced my 44 year old furnace. Over the years we have had several construction projects inside the home. For many years breathing the heated air from the duct work caused excessive sneezing, sinus issues, and lung irritation. . The heat smelled like dust. To maximize air quality I added a humidifier, MERV-11 filter, and UV light onto the new furnace. To further improve air quality, I had the ducts cleaned and sanitized. I took before and after pictures of the inside of each return and output duct. They were filthy before, and sparkling clean and fresh after the procedure. Now when running the system, clean sanitized air flows through my whole house. A huge difference. It will make sleeping and being indoors during the winter months far more tolerable. I use window air conditioners, and run the system in the summer to keep the house air clean and fresh on hot summer days too. It works! Great decision!
On the other hand, if a service provider fails to follow proper duct cleaning procedures, duct cleaning can cause indoor air problems. For example, an inadequate vacuum collection system can release more dust, dirt and other contaminants than if you had left the ducts alone. A careless or inadequately trained service provider can damage your ducts or heating and cooling system, possibly increasing your heating and air conditioning costs or forcing you to undertake difficult and costly repairs or replacements.
Contact/Relay -- Relays are electronically controlled switches that activate the various components of your HVAC system. They manage everything from the power going to the motor to automatic dampers, humidifiers, etc. Most of them are controlled by the thermostat. The most common failure for a relay is being stuck in the "open" position. Separated from its assigned contact point, it fails to complete the connection and send the message to whatever it was supposed to operate. This failure usually occurs from use over time. Each time a relay connects and sends its signal, the electrical arcing from point to point eventually causes wear and tear.
Fresh-Aire UV is an innovation leader in the field of indoor air quality. Our award-winning UV light and carbon products fight mold, bacteria, viruses and odors in commercial and residential HVACR systems. Our products include Blue-Tube UV®, the worlds most popular germicidal UV light, the revolutionary APCO® PCO/carbon whole-house air purifier, and Mini UV the first UV light system designed specifically for mini-split AC systems.
He proceeded to clean each heat register by removing the grille and blasting it with an air pressure hose toward the duct opening thinking that the dust would magically be sucked inside. In one room this caused a ceiling smoke detector to go off because the excess dust fooled it into thinking there was smoke. I put my hand in front of a register he wasn’t working on and could hardly feel a suction. Although we discussed how I open and close damper doors, I realized later that he never checked, opened or adjusted them during the cleaning. He could have closed all but the one he was working on in order to increase suction results. His next step was to blast air into the duct and then attach a “squid-like” device that slapped around inside the duct as far as he could reach. This is important! In a newer house, ducts have long straight runs from the furnace. In older houses like mine they can turn and twist. In fact, the duct we have a problem with runs straight up from the basement inside a wall and turns 90 degrees into a soffit for three feet then into two 90 degree turns to get into the floor joist area for another two feet and finally a 90 degree turn up to the second floor register. When he cleaned this one he could only get three feet into the register with the hose or squid because of the turns. That was the case with most. Hardly what could be described as a decent cleaning.
This is where i found where the major problem was for the dust problem in my home. I took down the sheet metal that was 16" wide down by taking the screws out that keep it attached and when i took it down i, could not beleive the amountbof dust that was up there, inhad to put on breathing nasks to actually scoop out all the cust with my hads and then i used my shop vac then bleached everything, i would say that i filled up a 5 gallon maybe more not counting all the dust that was attached to the side of the beams that was all wood , because the contractor did not actually build a 16" wide return all out of metal , butvinstead used the sheet metal plate as a short cut to make a suare box using my beams in my basement to make a suare box. I was told contractors do that often and i feel that should be outlawed because it caused my sinus and allery problems,nwhich almost caused me to die. so everyone should make sure their ductwork was made properly. Yes seal it . Cover all openings. So it was not the contractors fault that my vents still had dust, in them, he was afraid tomgetvon top of my pool table to try to get iside the short cut ductwork with the 16" wide sheet metal. To everyone, make sure you clean your vent system. And make sure you could see it visually like i did , neither i or the contractor had no clue the problem was right above my pool table because of the make shift ductwork. The contactor shoul have made a squrae duct like the rest instead of using my beams as a short cut. That could be whyba lot of people start to have major allergy problems and maybe even ashma.so coverall holes to prevent dust to be taken in and all bugs etc. then make sure you clean your ductwork as you see reasonable, they say every 5 years , but i say evry 2 to 3 years, but you can do it yoursely.. You need a good air hose and suction vacum like a shop vac, do a little research. I invented something a while back like 18 to 20 years ago , and now it is on the market to help homeowners such as ourselves with this dust problem. I cannont say anymore because i have to make sure that it was not my research and idea that solved my problem and for all the others that are using what i invented ..there was nothing on the patent search that i hired an invention company to do, back then. Once yor vents are cleaned properly younwill be very happybif you are an allery sufferer. Stop the children for throwing things into the ductwork and sweeping things into the ductwork, keeping your vent system is clean once youbclean it right the first time, just maintain it , you dhould keepmthe hvac system clean such as coils etc it truly helps,people vome into my condo and they cannont beleive how cold it igets and how my system works so well. it is because i have my whole duct system sealed outsid with the duct sealant and my coils i vleaned my self and take the time that the furnase fan is cleaned because that could have a lot of major dust attached to it, mine had a lot of caked on dust it was like hard dirt. Yxounwill save on allergy bills nasal sprays, i wish I could say more because incould say something to really keep your whole duct system clean for years once you do a first good cleaning of intake and return vents. until i email one of the major companies to see where they got my idea from. Intrulybhope it was not from the invention company i hired years ago who did the patent search for my idea. I becam
If you believe that the AC's not working or you're getting little or no cold air, check these three things first. Make sure all the registers in the house are wide open. Then be sure the furnace filter is clean. Then go outside and clean off the condenser coils (Photo 2). If several registers were closed or the filter was clogged, the reduced airflow could have caused the evaporator coil to ice up and stop cooling your home. If you've changed the filter and opened all the registers and you're still not getting airflow at the registers, deice the A-coil. Move the thermostat mode switch from “Cooling” to “Off” and move the fan switch from “Auto” to “On.” Let the blower run for at least 30 minutes or until there's good airflow at the registers. Then turn the AC back on to test it. If it works for the next 12 hours, you've solved the problem.