I just had my Air ducts “cleaned”. The person who came to my house works for an air duct cleaning company who uses a professional vacuum. He said the company would charge me about $900 but he can do it aside on his own and charge me half of that. However, when he came over the house, he brought the rotary brush along with his domestic vacuum cleaner that it’s hose was about 5 feet long, I ask him that the wasnt strong enough to pull dust out, and he said, it’s similar to what companies use. I was in doubt and he didnt cover the vents so im thinking all dust must have come out from every air vents. Could this vacuum have taking the debris out of the air ducts? Or how can I myself find out if the inside of the air ducts have been cleaned and no debris is sitting there? I have dust all over my house.
AC units and thermostats have built-in delay features when they're shut down and then repowered. The delay can be as long as 10 minutes. And, if you've subscribed to an energy-saving device from your local power utility, the unit can take even longer to reset. If you've installed the parts shown and reinstalled the disconnect block, repowered the circuit breaker, turned on the switch at the furnace, moved the thermostat to AC mode and lowered the temperature below the indoor temperature, and the unit doesn't fire up after 30 minutes, it's time to call a pro.
As I type this, I am having my ducts cleaned. About 30 including returns and the furnace. $543.00. I am watching the team do it and can see the clear vacuuming tubing and how dirty it has become. I like the gentleman’s comment on “stick your head in your vacuum and breath”….I get it. The team showed me the machine and it’s filtration system…and they will show me it again after the cleaning. However, like I said before, I am actively seeing the tubing that is clear before they start and how dirty it is once they begin and continue cleaning. Reputable company and not a “fly by night” coupon service. People don’t be so cheap, that is your problem.
They were quick to come out and diagnose the problem with my furnace, but I thought the estimate of $549 a bit high to replace the circuit board. So called around and found Leo's Appliance in Concord that sells appliance parts and the circuit board was only $90.49 - that is the retail cost to me, so I imagine the wholesale cost is a lot less. So BEWARE of this company since they wanted $500!!! to replace the circuit board which is located right in the front of the furnace - extremely easy to access. I hate it that you cannot trust repair companies.
Energy efficiency can be improved even more in central heating systems by introducing zoned heating. This allows a more granular application of heat, similar to non-central heating systems. Zones are controlled by multiple thermostats. In water heating systems the thermostats control zone valves, and in forced air systems they control zone dampers inside the vents which selectively block the flow of air. In this case, the control system is very critical to maintaining a proper temperature.
Filtration systems -- A second-stage filter is sometimes inserted & used to remove particulates such as pets, smoking or cooking, as well as other odors, gases, and VOCs (volatile organic compounds). A HEPA filter is also available to remove spores, pollens, bacteria and lung-damaging particles. There are also systems that use ultraviolet (UV) light to protect against bacteria and germs.
Service Experts Heating and Air Conditioning was founded on the basis of providing customers with the best heating and cooling practices in the industry. Since its inception, Service Experts has been dedicated to community, providing the top of the line HVAC products and services in your area. If you want more information about your local HVAC leaders, call us at 866-397-3787 or set up an appointment with us online.
HVAC professionals in the US can receive training through formal training institutions, where most earn associate degrees. Training for HVAC technicians includes classroom lectures and hands-on tasks, and can be followed by an apprenticeship wherein the recent graduate works alongside a professional HVAC technician for a temporary period. HVAC techs who have been trained can also be certified in areas such as air conditioning, heat pumps, gas heating, and commercial refrigeration.
I am very interested by your post. We recently had a lead inspection on our property and one thing the lead inspector suggested was to get the air ducts cleaned out. We had our ducts cleaned last year after we under went a large renovation project (since we have a toddler in the house). This year we decided to go for lead compliance and had all our lead removed (we moved out for the work). Recently, my son had a false positive lead test, which prompted us to get a lead dust inspection around the house (including having the vents dust-wiped on the inside). The levels inside the ducts weren't crazy high (but more than would be acceptable for a floor). As it turned out my son's lead levels are very low (but not zero). Is it possible however that lead dust from the inside of a vent can come out? Would this be a scenario where you think air duct cleaning would be beneficial?
One problem occurred on Monday. When we called at 2:30 in the afternoon to check on status, we were told that "the tech is on the phone with the parts supplier now". It seems more likely that they had forgotten about us and our call woke them up. But even if true, why the heck did they wait until 2:30 to order the part? Maybe if they had ordered it in the morning they could have had it the same day. So I'm taking off one star for that.
I live in a 1950's ranch house in the South. The prior owners were smokers. Based on recommendations from one of the local conservation organizations, I decided to have a home energy audit done. As part of their findings, they recommended additional insulation in the attic and duct cleaning and sealing. This turned out to be a very problematic process. In terms of the ducts, it was necessary to remove the metal grates. However, these grates had been painted over many times and shoe molding covered the bottom of the grates. The vendor was not able to remove the grates without damaging them in the process. Because these grates dated back to the 1950's, it was difficult to find appropriate replacements. The ones I finally discovered were correct except they were 1/4" wider. This meant that the shoe molding had to be carved out. The duct cleaner could not provide any assistance with this problem. It took me a month of long evenings replacing the vent covers myself, carefully chiseling out the shoe molding and repainting. In terms of the extra installation in the attic, the same vendor used blow in insulation. Unfortunately, they did not recognize that the 13 floodlights whose mounting extended into the attic were not designed to be buried under insulation. The problem manifested itself in terms of expensive flood light bulbs failing continually. So, I had to have all of the light housings replaced. Yet another unexpected expense. Despite the expense, pain and suffering, I cannot report any improvement in my heating costs or the "quality" of the air. To be fair, I do not have any allergies and did not undertake this for air quality improvements but rather heating efficiency improvements.
Air conditioner size is measured in “tons.” However, the tonnage of an HVAC unit is not actually based on its weight. A “ton” is simply a measure of an air conditioner’s ability to cool your home. One ton is the ability of your air conditioning system to cool 12,000 BTUs (BTU stands for British Thermal Unit) in an hour. Likewise, a “2-ton” central air conditioner is able to cool 24,000 BTUs per hour.
Replacing a capacitor is easy. Just take a photo of the wires before disconnecting anything (you may need a reference later on). Then discharge the stored energy in the old capacitor (Photo 4). Use needle-nose pliers to pluck one wire at a time from the old capacitor and snap it onto the corresponding tab of the new capacitor. The female crimp connectors should snap tightly onto the capacitor tabs. Wiggle each connector to see if it's tight. If it's not, remove the connector and bend the rounded edges of it so it makes a tighter fit on the tab. When you've swapped all the wires, secure the new capacitor (Photo 5).